It is a few weeks that I have noticed and increasing loss of water pressure. Everything started three weeks ago, when I decided to stop the heating of the house since it was getting warmer and warmer. In that occasion I discovered that the pressure was lower of almost 0.5 bar.
I have already spoken with the plumber but he is not too sure about the reason why our heating system is loosing so much water in such a short time without leaving any kind of traces on walls, floor, whatever.
Now I have filled the system again in order to reach a pressure of about 2 bar. I’ll keep observing the manometer and see how fast it declines.
Before adding water pressure is about 1.5 bar
After, pressure is about 2.0 bar
I’m starting to think that the expansion vessel might be not working correctly anymore. The name of the make is Pneumatex, while the model is Statico SD80.3. Here some further specifcations.
Many weeks later I decided to try to solve the issue: have a look at the follow up!
This year I had a few issues with our heating system at home: I’m going to describe what happened and what I learned from my little incidents.
Description of the heating system
Based on our experience, we decided to install an underfloor heating system when we built the new house, therefore we do not have any radiators to be seen: the heat is carried by a liquid which is constantly pumped through tubes running under our floor. The burner is a gas powered Remeha Calenta 35S+. We bought it and installed it during 2011.
I have understood that the “+” in the model name refers to the fact that this burner is built for the preparation of hot water to be used e.g. in the shower as well as the heating. Other models like the “35” have been developed for the heating system only.
Manuals for the burner (sadly in Italian language only, I wasn’t able to find them in English).
The burner has a second computer on board, the so called PM 2975 OGZ, which is dedicated to the control of the temperature of the heating, of the hot water, the scheduling… Sadly I have lost the manual explaining how this particular computer should be set. In any case I remember it wasn’t that clear.
One example that explains the role of the PM 2975 OGZ is the following: the PM 2975 OGZ uses a temperature probe installed outside the house to measure the outside temperature and based on this information and on an algorithm it increases or decreases the heating temperature.
Every year let the company perform the maintenance of burner
Every year have the chimney sweep clean the burner
Every three years have the plumber clean the pipes of the underfloor heating
Every five years have the boiler cleaned
During the year it is a good idea to check the pressure of the liquid in the circuit. It is known that the pressure may go down so that once or twice a year a refill needs to be made. The refill is usually done with water: you should take care of refilling slowly and avoiding air to get into the tubes. To do that it is recommended to add water into the refilling tube until it is completely full before opening the tap and letting the fresh water into the circuit.
The recommended pressure is around 2 bars in the winter time, when the heating system is on, while in the summer the pressure may lower to 1.5 bars.
Why is it important to have the chimney sweep clean the burner?
Because of my ignorance I never called the chimney sweeper for 5 years: I was convinced that the regular maintenance performed by Elco was the only one regular maintenance to be made. But I was wrong. This year we realised that the heating system wasn’t capable of reaching the temperature we wanted while outside the temperature was going below zero. Also the water for the shower was hot, but not as usual. Therefore I started to worry and called Elco, announcing that the burner wasn’t working properly. As the technician arrived we checked the methane consumption over a period of time of some seconds and quickly he was able to tell me that the burner was working at a third of its capacity. Then he disassembled the whole burner and he discovered that it was clogged and that needed to be thoroughly cleaned. The Elco technician made what he could in order to start the burner again and on the first days of January I called the chimney sweeper.
As per the moment being everything works fine: the shower is hot enough and the heating works fine. Pressure in the tubes is around two bars.
The one thing I have realised is that the burner needs attentive care and should be checked ever now and then, maybe a quick look every month, in order to see if everything works fine or at least have a date to refer to, in case something suddenly stops working correctly.